All regulated tanks must have leak detection (often also called release detection) so that leaks are discovered quickly before contamination spreads from the Underground Storage Tank (UST) site.
You must provide your UST system with release detection that allows you to meet all four basic requirements:
Additional information on the EPA UST requirements can be found at https://www.epa.gov/ust. State and local regulations may differ from the federal requirements. Contact your local agency to ensure that you are meeting all requirements.
Any one method of release detection has the potential to miss an event, or its magnitude, if solely relied upon. It is best practice to build a system with multiple release detection methods incorporated and manage it through the Automatic Tank Gauge.
State and local regulations may differ from the federal requirements. Contact your local agency to ensure that you are meeting all requirements. 1. Automatic Tank Gauging
2. Monitoring for Vapor in the Soil
3. Monitoring for Contamination in Groundwater
4. Interstitial Monitoring
(For tanks installed after April 11, 2016, Interstitial Monitoring is the only permissible release detection method.)
5. Statistical Inventory Reconciliation [SIR]
6. Weekly Manual Tank Gauging
(Only valid for tanks less than 2000 gallons)
7. Annual Tank Tightness Testing and either Daily Inventory Control or Manual Tank Gauging
(Only valid for tanks less than 10 years old)
An automatic tank gauge (ATG) system detects leaks through highly accurate inventory measurements combined with the tracking of delivery and dispensing activities.
Vapor monitoring senses or measures fumes from leaked product in the soil around the tank to determine if the tank or underground piping is leaking.
Vapor monitoring is not recommended as sole method for compliance because of the delay in detection and potential for wet sensors. By the time the vapor sensors go to alarm, the contamination has likely already occurred.
Groundwater monitoring involves the use of permanent monitoring wells placed close to the underground storage tank (UST). The wells are checked at least monthly for the presence of product that has leaked from the UST and is floating on the groundwater surface.
Groundwater monitoring is not recommended as the sole method for compliance because of the delay in detection. By the time the sensors go to alarm, contamination has likely already occurred.
Interstitial monitoring requires secondary containment, like a double wall tank or double wall piping, which provides a barrier between the tank or piping system and the environment. The barrier holds the leak between the tank and the barrier so that the leak is detected.
For tanks installed after April 11, 2016, Interstitial Monitoring is the only permissible leak detection method. The interstitial monitor must be checked at least once every 30 days.
The interstitial sensor needed will depend on the type of secondary containment barrier and the tank material being used.
Statistical Inventory Reconciliation (SIR) analyzes inventory, delivery, and dispensing data collected over a period of time (30 to 60 days) to determine whether or not a tank system is leaking
This is the manual measurement at the beginning and end of a designated quiet period (when no liquid is added/subtracted).
This is a combination of two practices: Tank tightness testing and inventory control.
Any one method of leak detection has the potential to miss an event, or its magnitude, if solely relied upon. It is best practice to build a system with multiple leak detection methods incorporated and manage it through the Automatic Tank Gauge.
Reports must be printed or archived every 30 days
Certified leak-testing technology that continuously monitors fuel height and temperature to detect idle times in underground storage tank and collects data for leak detection.
Leak detection and monitoring sensors for double wall tanks and brine reservoirs
Sensors for groundwater and vapor monitoring wells
Magnetostrictive probe technology provides storage tank owners a highly accurate device to measure and transmit inventory levels, water height and temperature to a monitoring device. See the available options.
Leak detection and monitoring sensors for containment and dispenser sumps
The TLS-450PLUS automatic tank gauge provides the most comprehensive fuel site data for advanced fuel asset management.