The following technical support notification discusses programming the Overfill Alarm on the TLS-450PLUS automatic tank gauge. Only certified contractors should install or service Veeder-Root products. Download the technical service notification as a PDF.
The Overfill Alarm is an external device mounted near the tank pad. During a delivery, if a tank is overfilled, the Overfill Alarm unit will activate a light and buzzer to notify the delivery driver to stop filling the tank. The instructions below are for use in conjunction with the Overfill Alarm Installation Guide (576013-589).
a. Configured: Enabled
b. Assign an Address
c. Label: Overfill Alarm
d. Type: Standard
e. Orientation: Normally Open
Automatic Event Setup
a. On the left side of the screen, select: Actions > Add Task
b. Device: Select the relay (Overfill Alarm)
- Scroll down for TANK, select the triangle to expand for additional options.
- Scroll down for OVERFILL ALARM, check off the box to enable all tanks.
- When complete, select the blue check mark to save.